2009 Rhode Island Code
Title 46 - Waters and Navigation
CHAPTER 46-13 - Public Drinking Water Supply
§ 46-13-7 - Tanks connected to unsafe supplies.
§ 46-13-7 Tanks connected to unsafe supplies. Any person who maintains a public water supply system connection to a tank which is also supplied with water from a water supply system found by the director to be unsafe, shall maintain the tank open to atmospheric pressure, and the public water supply pipe shall terminate at least two (2) pipe diameters above the maximum level of water in the tank. The tank overflow shall be of adequate size to fix definitely the maximum level.
Disclaimer: These codes may not be the most recent version. Rhode Island may have more current or accurate information. We make no warranties or guarantees about the accuracy, completeness, or adequacy of the information contained on this site or the information linked to on the state site. Please check official sources.